Find great deals for Gamewell Flex If LCD Display With CPU Fire Alarm Board ASSY If Shop with confidence on eBay!. The Gamewell Retrofit Kits offered by Gamewell-FCI provide a simple way to convert without replacing the existing Gamewell backbox. IF panel. Gamewell IdentiFlex Fire Alarm Control Panel. FIRE ALARM AND SMOKE DETECTION SYSTEM. 1. GENERAL. RELATED DOCUMENTS.
|Published (Last):||18 August 2017|
|PDF File Size:||7.93 Mb|
|ePub File Size:||12.71 Mb|
|Price:||Free* [*Free Regsitration Required]|
Gamewell System Obsolete?
Anyone who tells you all their jobs are perfect is full of SH1t. Gamewell has been around forever, I’ve seen some really old systems by them that are probably obsolete. You do not have the required permissions to view the files attached to this post. This card is made to run the older Gamewell Apollo XP95 devices. Did you miss your activation email? There are replacement parts available though.
You get the picture. It is a Gamewell System model IF Tue Sep 23, I don’t know if they’re still in business as the company making the city master fire alarm boxes but the fire alarm panel line became Gamewsll and then got swallowed up into the Honeywell cluster. January 16, Now a few years later the system gets swapped out with an E3 system and all gamewelll a sudden there is tamewell extra address trouble on the panel.
If you have any Q’s let me know. Read times schoolguy Member Posts: You cannot post new topics in this forum You cannot reply to topics in this forum You cannot edit your posts in this forum You cannot iif610 your posts in this forum You cannot post attachments in this forum.
Most of the fire alarm builders have sunseted their older models, as a result. The ambient temperature is fairly warm though far from hot enough to gamewfll a legitimate alarm condition.
It is true that the, and panels are not made any more. This will indicate gmaewell ambient temperature of the machine room. Any ways the E3 will accomodate the Apollo devices and give you full control over the system and even more features.
That being said, what temperature rating sprinklers are installed? Gamewell IF heat detector false alarms Posted: Any advice would be greatly appreciated. Page gammewell of 1. Heat detectors associated with elevator control should always be fixed temperature only, not ROR, in order to activate prior to the sprinkler head.
• View topic – Gamewell IF heat detector false alarms
We have literally hundreds of customers that have older gamewepl systems in them. Can anyone comfirm for me that this panel is obsolete and explain what the usual life is for heat and smoke detectors in a gamswell. I’ve replaced the detector and now the base, but the issues continue. This way the customer has a system that is new and up to code as well as being able to purchase the apollo devices when needed.
The cost on parts for the is NOT going to go down but rather UP as parts become less and less available. Most of the colleges that have a lot of Gamewell systems have a decent ammount of spare devices in stock in their maintenance area.
Not familiar with that model, but chances are, he’s right. That said There is a new read 2 to 3 years old panel out that you may want to look into. Mon Dec 31, 3: We have had no issues servicing them so far.
They merged under the Honeywell umbrella. I am in charge of a large school building and am being told that my fire alarm panel is obsolete and that parts are not available. Make sure the heat detectors are rated for the same environment. SMF – Just Installed! Further, the rate of rise is consistent with the second tower on the property, which is not having this issue. IF that is the case, then would anyone happen to have the software that I need to change the device address and the related functions in the program??
The location is inside the elevator machine room on the roof top of a 10 story tower gamesell Long Beach.
Previous topic Next topic. Now there is ventilation provided by an exhaust fan and two open-air elctro-mechanical dampers, all of which are open and running.
Gamewell If610 GW31025 Bus Driver Signal System Control Module
Yes this really happened to me a few months ago. You can’t win; you cant’ break even; and you can’t id610 out of the Game. Recently, UL updated it’s fire alarm standards from 8th edition to 9th edition. Either way I would look into the E3 as a solution for the Gamewell Gamewell IF heat detector false alarms. The GW will not show a trouble or anything system normal.
Please login or register.
The Truth of Thermodynamics: January 15, ,